LFS-W1B-XX* 1 Button
LFS-W2BS-XX* 2 Button
LFS-W3BS-XX* 3 Button
LFS-W3BSRL-XX* 3 Button, Raise/Lower
LFS-W4BS-XX* 4 Button
LFS-W4S-XX* 4 Scene, Raise/Lower
LFS-W5B-XX* 5 Button
LFS-W5BRL-XX* 5 Button, Raise/Lower
LFS-W6B-XX* 6 Button
LFS-W6BRL-XX* 6 Button, Raise/Lower
LFS-W7B-XX* 7 Button
LFS-W1RLD-XX* Dual Group, Raise/Lower (1)
LFS-W2RLD-XX* Dual Group, Raise/Lower (2)
LFS-W3BD-XX* Dual Group
Power 24 V- 30 mA IEC PELV / NEC® Class 2
Typical Power Consumption0.6 W; 1 Power Draw Unit (PDU)
Test conditions: all backlights on medium intensity, two LEDs on (two presets active), keypad powered at 24V
Environment Ambient operating temperature: 32 °F to 104 °F (0 °C to 40 °C), 0% to 90% humidity, non-condensing. Indoor use only.
Communications Connects to QS wired device link on HomeWorksR QS processor.
ESD Protection Tested to withstand electrostatic discharge without damage or memory loss, in accordance with IEC 61000-4-2.
Surge Protection Tested to withstand surge voltages without damage or loss of operation, in accordance with IEEE C62.41-1991 Recommended Practice on Surge Voltages in Low-Voltage AC Power Circuits.
Power Failure Power failure memory: should power be interrupted, the keypad will return to its previous state when power is restored.
Mounting Signature SeriesT Wallbox P/N WBOX-SA1-Q1 (sold separately) 4.45 in (113.03 mm) tall by 1.55 in (39.37 mm) wide by 2.8 in (71.12 mm) deep.
Wiring Control wire must be 1 pair 18 AWG (1.0 mm2) IEC PELV / NEC® Class 2 for power and 1 pair 22 to 18 AWG (0.5 to 1.0 mm2) IEC PELV / NEC® Class 2 twisted/shielded for data